Relative humidity sensor dial
OFF / 60% / COMFORT ZONE / 30%
Overrides the ventilation system to high speed once the level of humidity is above the set point.
If the wall control is in CONT or INTERM mode the ventilation system will automatically return to its original mode once the level of humidity is below the set point.
OFF – Sends command to shut down ventilation system.
NORMAL – The ventilation system operates on installers set speeds (CONT and OVERRIDE).
REDUCE – The ventilation system operates at 30% reduction in CONT and OVERRIDE speed.
Note: REDUCE mode will not decrease below the maximum low speed of the ventilation system.
INTERM – Ventilation is halted meaning,automatically stopping and starting at intervals the ventilation system from a command from a remote wall controls.
RECIRC – The recirculation mode recycles already-heated ambient air from a selected area and distributes throughout your home. This enables the ventilation system to have an auxiliary air supply automatically during defrost sequence or when RECIRC mode is selected.
CONT – Provides a continuous ventilation rate. The ventilation system will increase to high from command of remote wall controls.(Recommended for maximum indoor air quality.)
Orange light = ON (CONT / INTERM)
Green LED light = OVERRIDE (MAXIMUM SPEED)